coastin, the house is a great place to be with -6 outside.
I found something interesting in the heat loss area, I removed the cold air vent for the first time to look at the furnace and found thatoneof the flexhose was not hooked up to theadapter and was laying on the floor.
The adapter wasloose and just hanging there,the furnace was just blowing hot air under the sinkto the pass through space.
After this was completed I noticed that the end plate that held the two adapters and flex pipes, on one end it was not put all the way on the furnace so I corrected that but,I feel a lot of hot air being blowing out on that side of the end plate.
My question is this normal? if itis not, that would also be anotherreason I am not getting enough air to the flex pipes.